Operating gate motors Momentary switch After releasing the switch a spring automatically pushes back and disconnects the switch. This parameter is not relevant in gate operating modes parameter 151 set to 3 or 4. Change switch state — initiate down movement. Correctly configured slats should not force the blinds to move up or down. Visual indicator glowing red — the device is not able to connect to the main controller directly or through another Z-Wave network device repeater. Removing Exclusion — Z-Wave device learning mode, allowing to remove the device from existing Z-Wave network. The parameters consist of 4 bytes, three most significant bytes are set according to the official Z-Wave protocol specification.
The parameters consist of 4 bytes, three most significant bytes are set according to the official Z-Wave protocol specification. For modes with positioning value is set automatically during calibration, otherwise, it must be set manually. Electric active power — power that energy receiver is changing into a work and heat. Z-Wave network Adding the device Adding Inclusion — Z-Wave device learning mode, allowing to add the device to existing Z-Wave network. After 2 seconds the device will retry to establish a direct communication with the main controller, which will be signalled with visual indicator pulsing green.
Communication mode of the device may switch between direct and one using routing, especially if the device is on the limit of the direct range. Visual indicator glowing green — the device communicates with the main controller directly. Opening the contact will stop the gate. Consumers of electricity in households are billed by suppliers on the basis of active power used in given unit of time. The parameters consist of 4 bytes, three most significant bytes are set according to the official Z-Wave protocol specification.
The device is equipped with power and energy monitoring. Hold switch — initiate slats rotation up. Menu Menu allows to perform Z-Wave network actions. Additional features Power and energy consumption The device allows for the active power and energy consumption monitoring. Power reports are sent no often than every 30 seconds. Periodic reports do not depend on energy change parameter 65.
Hold switch — initiate slats rotation down. The parameter relevant only if the device is set to work in positioning mode parameter 151 set to 1, 2 or 4. Testing may stress the network, so it is recommended to perform the test only in special cases. Z-Wave range tester signalling modes: Visual indicator pulsing green — the device attempts to establish a direct communication with the main controller. If the blind is moving, clicking any button, will stop the movement.
The procedure consists of an automatic, full movement between the limit switches up, down, and up again. Toggle switch Operates as a two-position switch, it has no spring that would set one position of the switch. Electric energy — energy consumed by a device through a time period. Resetting to factory defaults Reset procedure allows to restore the device back to its factory settings, which means all information about the Z-Wave controller and user configuration will be deleted. This parameter defines as what type the device should treat the switch connected to the S1 and S2 terminals. Gate motor should be connected to Q1 and Q2 terminals according to installation diagram. Positioning calibration Calibration is a process during which a device learns the position of the limit switches and a motor characteristic.
In this case switch always works as a momentary and has to be connected to S1 terminal. Dimmer, Relay Switch, Roller Shutter or scene may be controlled only through a Z-Wave controller. The parameters consist of 4 bytes, three most significant bytes are set according to the official Z-Wave protocol specification. Certain device removal can be achieved by the procedure of removing described in Adding the device section. Roller Shutter 3 allows precise positioning of roller blinds or venetian blind lamellas. Choosing a middle position stops the blinds. Opening a contact in a device connected to S2 terminal will always result in stopping a motor in current position.
If a direct communication attempt fails, the device will try to establish a routed communication, through other modules, which will be signalled by visual indicator pulsing yellow. Connecting the Roller Shutter 3 in a manner inconsistent with this manual may cause risk to health, life or material damage. To make Z-Wave range test possible, the device must be added to the Z-Wave controller. Visual indicator glowing yellow — the device communicates with the main controller through the other modules. For gates parameter 151 set to 3 or 4 the parameter determines the time after which the gate will start closing automatically if S2 contacts are opened if set to 0, gate will not close. Data is sent to the main Z-Wave controller. Operating the device Operating roller blinds Momentary switch After releasing the switch a spring automatically pushes back and disconnects the switch.
Available settings: 0-90000 0 — 900s, every 0. Removing the device restores all the default parameters of the device, but does not reset power metering data. Visual indicator pulsing violet — the device does communicate at the maximum distance of the Z-Wave network. The device allows to operate gate motors. For gates parameter 151 set to 3 or 4 the parameter determines time after which open gate will start closing automatically if set to 0, gate will not close. Periodic reports do not depend on power change parameter 61.
The parameters consist of 4 bytes, three most significant bytes are set according to the official Z-Wave protocol specification. If connection proves successful it will be confirmed with a yellow glow. When operating gates a momentary switch may be connected to S1 terminal. Association linking devices — direct control of other devices within the Z-Wave system network e. For loads under 50W, the parameter is not relevant and reports are sent every 5W change. In emergency, pushing the emergency stop button will cut the power and stop the gate. .